The TASSU S underfloor heating cables are used in plasterboard floors, wooden floors and in renovation, where the cable is installed on top of the old floor. The output per square meter should be 60 – 110 W/m², the installation distance 9 – 17 cm and the installation depth 2.5 cm. The heating cable is a preterminated twin-conductor cable with a PVC sheath. The lowest installation temperature is -10 °C. The output of the cable is 10W/m with a nominal voltage of 230V. The heating cable is supplied with a cold lead of 2.5 meter. Power below 80W/m² is for low energy houses (passive houses).